Construction Indoor Unit
shall be constructed from Anti Bacterial HIPS, certified to UL94 V0.
Closed cell foam shall be
used for insulation. The Outdoor unit
shall be constructed from galvanized steel with a baked on powder
coated finish for durability.
Exchangers The heat
exchangers shall be manufactured using diamond cut aluminum fin
mechanically bonded to copper
tubes. All heat exchanger fins shall be
coated with an hydrophilic and corrosion resistant finish.
Control shall be by a capillary tube located in the Outdoor unit,
refrigerant shall be environmentally
friendly R410A Compressors shall be a
hermetically sealed rotary type with external Overload protection
and suction accumulator.
Condensate Removal from Indoor Unit Shall be
accomplished via the standard 18" length Drain hose, can connect to
5/8" ID or 3/4" OD PVC tubing.
unit fan shall be molded from HIPS, statically and dynamically
balanced for quiet operation. Multiple fan speeds shall allow the
user to select the required airflow. An auto swing louver can be
either oscillate or be stopped in a user
selected position. The condenser fan shall be a propeller type with
a single or dual speed motor.
shall be operated via a hand held wireless remote control with a
range of 20ft.
shall be able to operate in the following modes:
Auto, where a default set point of 74 DegF (user
adjustable by +/- 2 DegF).
In Auto mode the Indoor unit shall determine the optimum fan speed.
Cool mode shall feature user selected room temperature and fan
Dry mode shall be akin to the cooling mode, except the Indoor fan
speed shall be factory preset for optimum de-humidification.
Fan mode shall just feature operation of the Indoor fan at a user
The unit shall feature a real time timer feature allowing a single
on or off operation to be programmed for a
A sleep feature shall reduce indoor airflow for quieter nighttime
Room temperature shall be sensed by a thermistor mounted on the
Indoor unit coil, directly in the return air
Indoor coil temperature shall be monitored to prevent the indoor
coil from freezing up due to lack of
airflow or a refrigerant loss.
All units shall feature Auto restart in the event of a power
Control voltage is line voltage 115V or 208/230V depending upon
unit power supply.